HMI screen for VFD control cabinet
Model : PD HMI
Brand : aikon
The software is a new configuration software product developed by our R&D team for three years. It was produced with more than ten years of technical experience and accumulation based on sufficient practices on man-machine interface product development and field actualization. We believe you will feel our specialization and concentration when you use this software.
Electrical connection of the screen
1.Connect to the power supply
The rated voltage of the screen is DC18~28V, and DC24V power supply is recommended. The interface is at the back, as shown in Fig. 1, the“24V+”is connected to“DC24V”, the“24V-“ (or "0V") is connected to “GND”. If the field is involved with a high interference, a highly reliable earth must be connected to the“FG”port. (Note: FG- Frame Ground, the reference grounding for the metal shell frame and the DC end.)
2.Connect to the computer
The screen can be connected to the computer only via a USB data cable for project uploading and downloading, as shown in Fig. 2.The communication with computer can be realized when it is connected to the “USB SLAVE” end. The USB communication drive can be installed by the system in default during software installation, or the drive can be manually installed if it is damaged.
If you want to learn more about the settings,
please click here to watch our video for general steps.
Project for 3 pumps without DTU Ver.B.0116.001
We're great at application issues, and we carry good stocks for quick delivery.
Contact us by E-MAIL：firstname.lastname@example.org
Or hit one of the contact methods on the right of this site.
We'll be glad to get a technician to talk with you about your VFD problems.